Tanks should be fitted with:
If upgrading an existing system or harvesting additional downpipes, tanks are usually but not always retro-fitted with an additional larger gate/ball valve. This is an opportunity to also de-sludge the tank.
Fitting is normally a quick and easy task but the tank’s distributor or manufacturer should be contacted if the homeowner does not feel confident or cannot access the necessary tools. Check with the manufacturer if in doubt about fitting an additional outlet to any section of the tank.
SUPADIVERTA delivers good quality water and one downpipe often supplies a class 9 PVC 25mm (30.5mm ID) pressure pipe diverted to an existing 25mm inlet.
Large tanks harvesting multiple downpipes sometimes have more than one inlet.
Many poly tanks have thicker wall sections where tank fittings are best fitted. NOTE that the hole saw size will be different to the outlet’s designated size.
1mm of water on 1 square metre = 1 litre
10mm rainfall per hour on 35 square metres of harvested roof is an average of 5.8 litres per minute.
The Australian Guidelines for Water Recycling specify that water diverted into a tank must pass through insect proof mesh with apertures no larger than 1mm.
Many areas of Australia have additional local council and health department requirements that state that mosquito proof meshed rainheads/leaf diverters must be fitted to rainwater harvesting systems that retain water in the pipes or fittings.
Supadiverta satisfies these requirements with its .75mm leaf diverter/ filter that also mosquito proofs the reservoir.